High accuracy and wide humidity measuring range.
Stable performance, supports long time use.
With large and clear display for better readability.
Two modes adjustable, dehumidification mode and humidification mode.
Applied to hatching device, refrigerator, greenhouse cultivation, freezer, ect.
Working voltage: 12V, 24V, 110V, 220 V (optional)
Measure range: 1%~99%RH
Measure accuracy: ±1%RH
Item size: 85 * 75 * 34.5mm / 3.35 * 2.95 * 1.36in
Package size: 100 * 85 * 50mm / 3.94 * 3.35 * 1.97in
Package weight: 127g / 4.48ounces
- ZFX-13001 Humidity controller
- Humidity senzor
ZFX 13001 humidity controller manual:
Wiring schematic diagram for ZFX 13001
1. The RST button is used to turn on / off the hygrostat. To control, press the RST button for 3 seconds
2. The SET button is used to set the desired humidity (short press for 1s). Long press of the button
SET is used to select between hygrostat functions.
3. Arrows ▲ ▼ are used to control the hygrostat, set the required humidity, select between
H – dehumidification, the hygrostat turns on the relay in dehumidification mode until the humidity drops to
the desired value, then gives the command to turn off the relay.
C – humidification, the hygrostat turns on the relay in humidification mode until the humidity reaches the desired
moisture, then it will give the command to turn off the relay.
By connecting the phase either to terminal 1or2.
CP-hysteresis, value by how much humidity can rise or fall to re-close the relay
hygrostat. If the hygrostat is set for humidification, for example, to the value 80% and the value for
hysteresis is 5, so the humidifier switches the relay on again only when the humidity drops to 75% (set value
80% – hysteresis 5 = 75%)
CA- Calibration – a function to adjust the accuracy of the hygrostat, if the CA value is +1, the hygrostat will be
show humidity 1% higher. If the value is -1, it will show a value 1% lower.
PU – delayed start – time function for the relay pick-up delay value 1 means that
the hygrostat waits one minute before turning on the relay.
HP – Select the alarm value according to how much the measured humidity can deviate from the set ac
deviates more, the hygrostat triggers an alarm.
• By briefly pressing the SET button, you set the target humidity with the up and down arrows
you increase and decrease the value.
Press the SET button for 3 seconds to get to the hygrostat menu where you can use the arrows
select items: HC,CP,PU,CA,HP press SET to select item with arrows set R.
Humidification: In the HC menu, select item C – humidification, the hygrostat will work in mode for
Then, in the item CP Hysteresis*, set the value by which the target humidity can decrease
Adjusted humidity – hysteresis
Example 55%-5%=50% You subtract the hysteresis from the target humidity and get the value at which
the hygrostat turns on the relay again. At 55%, the hygrostat switches off the relay and at 50% it switches on.
Dehumidification: In the HC menu, select the item H dehumidification, the hygrostat will work in the mode for
Then, in the CP Hysteresis* item, set the value by which the target humidity can rise
Adjusted humidity + hysteresis
Example 55%+5%=60% You add hysteresis to the target humidity and get a value at which
the hygrostat turns on the relay again. At 60%, the hygrostat turns on the relay and turns it off at 55%.